Construction of a container boiler room
Container dimensions: 4000x2200x2200 (LxWxH) in mm
Copper wires with a diameter of 28 mm
The return water temperature is controlled by the electronic three-way Rototemp 5/4 "
Pump 25-6 for the heating circuit of a building
Pump 25-4 for short boiler loop
Thermal comfort in the adjoining office building controls the ADEX Comfort R remote room thermostat. Radiators are fitted with thermostatic heads.
ESBE ARA 663 Actuator
Choosing the right container
For the construction of the container boiler room was used a light warehouse container with two-wing doors, which was insulated inside and fitted with plasterboard. The container boiler thus obtains the necessary insulation and also increases its aesthetic value. However, a shipping container of 20 feet or more may also be used.
The advantages of a container boiler room
Simple installation without any intervention in the building
Possibility of installation in buildings without boiler room
Possibility to connect a backup source
The possibility of using a storage tank with an internal boiler for hot service water
Possibility of installing the pellet hopper for the whole winter into the next container
Possibility to disconnect the boiler room and location in another location
Control of container boiler room
Switching the boiler pump is controlled by the boiler according to set temperatures. The short loop temperature is controlled by a three-way eletronic Valve Rototemp. The accumulation of the storage tank controls the upper and lower thermostat in the storage tank. The heating system is controlled by ADEX Comfort R electronics with equithermal regulation.